The Verkada AC41 Access Controller comes with 5 removable cassettes that are designed to make the installation and cabling process quick and easy. Simply remove the cassette, install the necessary wires into the cassette, and plug the cassette back into the AC41.
Before Getting Started
WARNING! – ENSURE POWER IS DISCONNECTED FROM THE AC41 AND LOCKING HARDWARE BEFORE WIRING READERS AND OTHER DEVICES. FAILURE TO DO SO CAN DAMAGE THE AC41.
Wiring fail secure and fail safe locking hardware
Be aware of the different ways to configure locking hardware, Fail secure and fail safe:
Fail secure locks require electrical power to unlock. In their normal unpowered state, they remain locked. They use a NO (Normally Open) circuit. Therefore, when power is interrupted, it will remain locked.
Fail safe locks require electrical power to remain locked. In their normal powered state, they remain locked. They use a NC (Normally Closed) circuit. When power is interrupted, it will unlock.
Keep in mind that some door strikes can be wired as fail safe and some electromagnetic locks can be fail secure; always check your third-party locking hardware wiring instructions and ensure you’re using the right configuration for your requirements.
Dry vs Wet
Dry - The AC41 does not provide power to the locking hardware (typically used with external power supplies)
Wet - The AC41 provides 12V or 24V power to the locking hardware
Best practice: Always use an external access power controller (Dry setup) when wiring up an ELECTROMAGNETIC lock (maglock).
Remove the cassette
Begin by removing a door cassette from the AC41 by lifting it from the side tabs. This will make wiring a breeze.
NOTE: Before you begin wiring your doors, please see the recommended wires for the AC41
Connect the Lock (Access Power Controller - Dry Contact*)
When using an Access Power Controller (APC) which uses a dry contact*, ensure that NONE is selected on the door power selection switch. The APC will detect if the AC41 relay is open or closed and translate that to the lock.
*Note: When the AC41 Door Power Selection Switch is set to None, the relay is not completely dry. The AC41 has the ability to power locks at 12V or 24V but as a result our relay is not completely dry. Isolation or common ground issues may occur.
Connect the Lock (Wet)
In a Wet configuration, ensure that power selection for each door is set to the correct voltage as outlined by the locking hardware specifications.
Set it to “12VDC” for 12 Volt locking hardware
Set it to “24VDC” for 24 Volt locking hardware
The AC41 is rated to power 12V locks up to 700mA and 24V locks up to 350mA.
Wet 12V / 24V NO-C
If you have a Fail Secure lock, connect to NO-COM where LOCK ( + ) positive goes into NO (fail secure) and LOCK ( – ) goes into COM.
Wet 12V / 24V NC-C
If you have a Fail Safe lock, connect to NC-COM where LOCK ( + ) positive goes into NC (fail safe) and LOCK ( – ) goes into COM.
Best practice: Always use an external access power controller when wiring up an ELECTROMAGNETIC lock (maglock). Do not use the Wet configuration!
WARNING! – When connecting the lock in the WET configuration, ensure the negative of the lock goes into the COM port as shown in the diagrams below. Polarity matters.
Connect the Reader
AC41 is rated to power readers at 12V up to 250mA via the + (VIN) and – (GND) connection. Verkada readers use the far left 4-port inputs while Standard Wiegand readers use the middle 6-port inputs.
The Verkada AD31 uses the following color scheme:
+ - Red
– - Black
A - Purple
B - Blue
Typical Wiegand wiring uses the following color scheme:
+ - Red
– - Black
D0 - Green
D1 - White
Note: Each door cassette can be connected to both a Wiegand reader and a Verkada reader. The AC41 supports simultaneous Verkada Reader and Wiegand connections.
Connect the Inputs
Both the DPI (Door Position Indicator) and the Request-to-Exit (REX) inputs are dry contacts. Installing these inputs is optional. They can be configured in Verkada Command.
Door Position Indicator (Door Contact), optional
NOTE: Verkada AC41 expects the DPI to be NORMALLY CLOSED (NC).
Request-to-Exit (REX), optional
The REX can be configured to release the lock in Verkada command (most commonly seen in electromagnetic locks) or simply shunt DFO (door forced open) events. The REX unlock time can also be configured.
NOTE: Verkada AC41 expects the REX to be NORMALLY OPEN (NO).
Powered Request-to-Exit (REX)
You may utilize the 12V port for the unused reader to power the REX device if necessary.
Wet configuration with emergency REX button release
Dry configuration with emergency REX button release
Insert the Cassette
To finalize the installation, insert the cassette back into the desired slot on the AC41. Then power the AC41 back on.